|Name:||Pex Reducing Coupling||Size:||1"×3/4'' Coupling Lead Free|
|Connection:||Push-fit||Application:||Quick Connect Fittings|
One Touch Connect Pex Reducing Coupling,
Quick Connect Pex Reducing Coupling,
1"×3/4'' Pex Reducing Coupling
Quick Connect Fittings 1"×3/4'' Pex Reducing Coupling
Pex Reducing Coupling Introduction
Note: JinQuan Fittings are available for higher temperatures, pressures.
Connects Copper,PEX and CPVC... pipe in any combination.
Pex Stiffener for PEX pipe only..
Approved for use underground and behind walls without access panels.
Certified for use in hydronic heating and potable water.
Push-Fit products are very convenient to install, just need to push the pipe completely into the fitting, needn't use any tools, such as spanner.
Pex Reducing Coupling Characteristic:
1) Made in brass material or carbon steel with nickel plated, and sealed with NBR
2) Easy to connect tube by one touch, and the is applicable for Polyurethane tubing and Nylon tubing
Pex Reducing Coupling Specification:
|Product name||Quick Connect Fittings 1"×3/4'' Pex Reducing Coupling|
|Material||Lead Free Brass body, non-toxic plastic push fit connection|
|Media||Water, oil, gas|
|Port Size||3/8", 1/2", 3/4", 1", 1-1/4", 1-1/2", 2"|
|Testing pressure||100% tested with 0.6MPa - 0.8MPa by air|
|Connection||Push fit x female thread|
|Valve guarantee||2 Years|
|Samples time||2 days - Current type
15 days - New mould
Pex Reducing Coupling Pictures
Select the correct size fitting and pipe for the job. Check that fittings and pipe are clean, in good condition and are free from damage and foreign objects.Cut the pipe so that the ends are square.Ensure that there are no burrs or damage to the cut end.Once the pipe end is cut square and clean,use a permanent marker to mark the insert depth on the outside of the pipe.This mark is used to ensure that the joint is assembled correctly.To assemble correctly,the pipe needs to be pushed into the fitting untill it meets the tube stop.Follow these three steps to insert the pipe into the fitting.
1.lnsert the pipe through the release collar against the grab ring.
2.Push the pipe firmly with a slight twisting action until it reaches
the tube stop.
3.To ensure that the pipe is correctly inserted, check that the depth
mark is within 0.005 in (0.13 mm) of the end of the release collar.
Disconnection of the joint can only occur by using the PUSHLOCK removal tool.By applying pressure to the release collar with the re-
moval tool, the grab ring teeth are splayed.This action releases the pipe, allowing it to be removed from the fitting.
1.Place the PUSHLOCK removal tool around the pipe with the non-
branded face against the release collar.The end with the size dis-
played on the removal tool should be positioned around the pipe and
the other end around the neck of the fitting.
2.Push the removal tool against the release collar and pull the pipe
with a twisting action to release the pipe.
3.Check the fitting and pipe end for damage.The fitting and pipe
should be free of damage, foreign objects and marks on the outside
diameter. If the pipe is damaged or marked, then cut and use a new
section of pipe.
Originally founed in1983,TaiZhou JinQuan Copper Inc. is one of the leading
manufacturer of lead free plumbing valves&fittings, mainly serving plumbing
wholesalers,distributors and retailers.
We are currently supplying lead free PEX fittings&Valves,push-fit fittings&Valves,
Various water supply stops and water connectors etc.All products are made of
lead-free with DZR functional brass,and have been certified and listed by IAPMO.
Our goal is to help our customers to increase their profitability and gain more market
share by taking advantage of our extremely competitive price and quality.
Contact Person: Sun